New Construction House Wire These are the most common electrical questions asked by our clients in the Yakima area. Contact us today at (509) 580-0470 so that we can discuss your electrical needs, since each electrical configuration and design is different we will study your case and provide an array of options.
(When is it time to call an electrician?)
When you are resetting circuit breakers or changing fuses too often. When you turn on your air conditioner and the lights dim in the room. When your lights flicker or go on and off. When you can smell wiring burning. When you have six electronic devices going into one outlet in back of your electronics center. When you have receptacle outlets overburdened by multi-plug strips. When a three-prong plug needs a two-prong adapter. If you have to run extension cords to plug in electrical devices.
What size service do I install in my home? Most states call for 100 amps minimum, but with all the new electronic devices, air conditioning and electric heat, We recommend 200 amps especially in new homes. This also gives you some space for future additions. This is not a job for an unlicensed person to attempt. In most cases it involves replacing everything from the service loop (this is the wire that extends from the top of your meter to the utility tie in ) up to and including the main panel..
(Where do you put G.F.I.'s?)
Any bathroom or garage outlet within 6' of a sink must be GFCI protected. The code also requires all kitchen outlets for countertop use to be GFCI protected. GFCI outlets must be installed in any area where electricity and water may come into contact, including basements, pools, spas, utility rooms, attached garages and outdoors. At least one GFCI outlet is required in an unfinished basement and for most outdoor outlets.
(The are two types of GFCIs in homes),
the GFCI outlet and the GFCI circuit breaker. Both do the same job, but each has different applications and limitations.
(The GFCI outlet is actually a replacement for a standard electrical outlet).
A GFCI is not dependent of a ground to function. It does not measure shorts to the ground, it measures the current difference between the hot and neutral wires. A sudden difference of 5 ma. or more, indicating that there is another path for the electricity to flow through will trip this device. The only downside to this is there may be some nuisance tripping in highly inductive loads like large motors or even fluorescent lamps or fixtures on the same circuit. But the newer models seemed to have corrected this somewhat.
It protects any appliance plugged into it, and can also be wired to protect other outlets that are connected to it. The GFCI circuit breaker controls an entire circuit, and is installed as a replacement for a circuit breaker on your home's main circuit board. Rather than install multiple GFCI outlets, one GFCI circuit breaker can protect the entire circuit. There is a test button and a reset button on these units. If you press the test button the reset should pop out. To reset just push the reset button in.
Not a good idea to put lights on GFCI. protected circuits so you aren't left in the dark if the circuit trips. Generally, equipment such as refrigerators, freezers and sump pumps that cannot go without electrical power for an extended period of time without causing costly losses or property damage should not be placed on a GFCI. protected circuit. GFCIs are very sensitive and are subject to nuisance tripping. GFCI receptacles don't last outdoors even under the best of conditions. Be sure to test the device using the "test" button before you use one.
How much should I attempt on my own? Doing electrical work yourself is a gamble. How much are you willing to risk to save money. There is a reason why it takes so much training to become an electrician. Do not make a mistake by taking electricity lightly, even the smallest job could be a safety hazard. Why take a chance.? Get a professional to do this work.
How many convenience outlets in each room? In every kitchen, family room, dining room, living room, parlor, library, den, bedroom, or similar room or area of dwelling units, receptacle outlets shall be installed so that no point along the floor line in any wall space there is more than six feet, from an outlet in that space. This is to prevent the use of extension cords. Outlets are usually placed about 18 inches above floor level. Switches usually go about 48 inches from floor level. For convenience outlets each single receptacle in a single branch circuit is usually figured for 1.5 amps, duplex outlets for 3 amps in estimating total amperage for that circuit. Air conditioners should be on a single dedicated circuit.
(How should outlets be installed)
New Construction House Wire Expound the actual teachings of the great explorer of the truth, the master-builder of human happiness. No one rejects, dislikes, or avoids pleasure itself.